Whole House System WH-002B-RF-UV (un-chlorinated water system for Tanks, Dams and soft water bores). This re-fillable carbon cartridge has silver nitrate impregnated carbon, if you use standard carbons in un-chlorinated water filter systems (without a UV steraliser) the carbon simply becomes a bacteria breeding ground, silver nitrate doesn't allow bacteria to grow on it's surfaces.
This systems first stage uses a 20" big blue housing with 1 or 5 micron polyspun sediment filter (your choice) The second stage uses a 20" big blue housing with a GAC silver carbon cartridge rated for 300,000 litres for chlorine and chemical treatment.
These housings are a Taiwanese copy of the Genuine PENTEK big blues and are certified to Australian Standard AS3497 and Watermarked. These Big blue housings are rated to 90 psi pressure and the system includes the two cartridges, two housings, powder coated wall bracket, housings are 1" thread.
This system uses a re-fillable carbon cartridge, this system is very cheap to run as the sediment cartridge and it costs $50 to change and just $60 for the 4 litres (2 kg) of carbon required to re-fill the carbon cartridge.
Stage 1- Sediment pre filter ( typically 5 micron) (1 " BSP female connections)
Stage 2- Ultraviolet sterilizer Top aqua 40 watt. 304 Stainless Steel (3/4" BSP male Connections)
Stage 3- Refillable silver impregnated carbon filter (1" BSP female connections)
Treatment rate specs:
Sediment treatment rate - 50LPM
1 x 40watt UV lights - 38LPM
Carbon Cartridge- 30LPM
Filter system dimensions of the installation pictured:
90 cm high x 90 cm wide x 21 cm deep
(Please allow and extra 850mm to the side for the uv bulb to be slid in and out of the stainless steel housing)
Sediment Pre filters 6-12months
Carbon filter 6-12months
Uv bulb 9000 Hrs or 12 months if running 24/7
Please note no piping or fittings are supplied with the filter system. These are an optional extra
2 x 25mm poly -3/4" Male BSP fitting ( installed onto sediment filter housing and carbon filter housing)
2 x 25mm poly - 3/4" female BSP fitting (installed onto UV housing)
2 x 900m long 25mm poly pipe (to pipe between sediment filter to UV and UV to carbon filter)
2 x 1"- 3/4" reducing bush (installed into sediment & carbon filter housings)
No fittings are supplied In and out of the system.